Our best selling 2 timings 3 switch sequencer!!
Packard heat sequencer consists of a tall tower and a short tower on one plate. 2 timings and 3 switches. The timings will come on (get hot) in 1-110 seconds (H1-110) and shut off (get cold) in 1-110 seconds (C1-110). The purpose of the timings is to turn on the heating elements in a sequence as to prevent a huge power surge which may blow a breaker.
If your electric furnace isn't putting out enough heat, it may be that the switches in your old sequencer aren't closing. Or if it feels like an element is not shutting off, a switch in your old sequencer may be stuck closed. Same can be said about the blower motor. If the motor doesn't turn on or shut off, it may be an issue with the first switch (M1-M2). Be sure to doublecheck the wiring diagram of your furnace as some models use the sequencer differently.
On a typical electric furnace, the blower motor is hooked to terminals M1 & M2 (perhaps referred to as H1 & H2 on other various sequencers). The heating elements are then hooked to M3-M4 and M5 -M6. 24V feeds the bottom (gold) terminals of the sequencer. Welded jumper bars connect the 24V from one tower to the next. If your application does not use these jumpers, simply twist them off with a pliers.
Not all the terminals of the sequencer may be used in your application. In some cases, you may need extra terminals. If that happens, included are extra terminal adapters to convert one terminal into two.
These sequencers are inexpensive and are ideal for replacing expensive OEM sequencers. But keep in mind there is some slight differences in the number of terminals and some adapters have been included to compensate for that. If you are not comfortable with that, then do not order. Instead order the exact OEM replacement which we also stock.
All our parts have a 1-year exchange warranty with us (no dealing with the manufacturer), so buy with confidence. We generally ship replacement parts the day you contact us.
This sequencer is the replacement for the following: Coleman S1-02435341000, 024-35341-000, 3400-357, 3400-3571, 3115-357, 3115-3571 & 3115-3571R; Nordyne 01-0842 & 621678; Goodman B1256553, B12565-53 & L41-691; Honeywell R24CB4007 & L39-278; White-Rodgers 24A34-5 & f77-5413; Global 24ZC-5; Mars 33232 & 33832; Klixon 51172-32; Diversitech DGS105; Gemline GS105; Interstate Electric IES24A34-5; Napco NS105; Packard HS24A345; Supco Q105; Watsco TDR30 & Zettler ZC24A34-5.